Thermal power radiators dia norm, it is the power released radiator provided: 1 – The temperature of the coolant entering the radiator 75 * with. 2 – The temperature of coolant at the exit from the radiator 65 * with. 3 – The atmospheric air pressure 1013 mbar. 4 – Average air temperature 20 * to. For other conditions of temperature and reverse connection or connecting a special valve (as in this connection is a significant reduction in power) require recalculation of thermal power.
Another of the conditions for calculating the heat capacity is the location of the radiators at a distance of approximately 110 mm from the floor and set free on a wall without a window sill. If these conditions are not met (the radiator is in a niche or distance is more or less from the floor) must take into account power reduction radiator. After a thermal power required is designed radiator can be proceed to their installation. There are several ways to mount radiators: 1 – With aid kit for quick installation, which includes screws planted clutches. Height adjustment is on top with a screwdriver screw, which rests on the sleeve, dressed in the screw.
2 – With spring anchorages – spring locks keep the radiator for its longitudinal edges. 3 – With floor mounting – allows you to mount the radiator without use of the wall. 4 – With the help of anchor bolts with eccentric – for installation of radiators with a variable distance to the wall. We have considered several kinds of mounting heat sinks, as there are several types of connections, look at them: 1 – Lateral connectivity and – a diagonal connection – delivery pipe connected to the upper nozzle, and the reverse to the opposite bottom. It is recommended when the length of the radiator is four times greater than its height or for longer than two meters. b – Lower Cross-connection – used when the tube wiring is hidden in the floor. Minus such a connection loss of power radiator. a – single-bore connection – if you use special valves. r – one-sided connection – delivery pipe connected to the upper branch pipe radiator and the back to the bottom. This is the most frequent solution to connect the radiator to allow poklyuchat radiators as with left and right side. It is for this method of connection is the nominal power calculation. 2 – Lower connection and – For one-pipe heating systems – not the most effective. b – For heating systems – the most efficient connectivity, which allows to achieve uniform heating radiators in the system. in – Lower connection at floor level. Radiators dia norm can effectively otoplivat estates in different ways connection and installation.